The PAD100-OROI uses one (1) SLC loop address when monitoring one (1) Class B circuit and providing one (1) Form C relay contact. The module mounts on either a 4" square or double gang box. The module is capable of monitoring one (1) Class B circuit. The PAD100- OROI includes one red LED to indicate the module's status. In normal condition, the LED flashes when the device is being polled by the control panel. When a the input is activated, the LED will flash at a fast rate.
ThePAD100-OROI is compatible with Potter's IPA series addressable fire alarm control panels. The PAD100-OROI is an interface module used to monitor dry contact devices such as sprinkler waterflow, valve tamper switches, or conventional pull stations. The module is capable of monitoring one Class B circuit. The PAD100-OROI also provides one (1) form C relay contact.
Setting the Address
Each addressable SLC device must be assigned an address. The address is set using the DIP switch located on the PAD100-OROI. When the PAD100- OROI is used to monitor one Class B circuit a single device address is assigned, the input and relay are then identified as a sub-point of the module address. For example, if the address number is assigned as "8", the RLY1 relay will be "8.1" and the IN1 input will be "8.2"